Acty Somonas (Ammonia removal)
● Ammonia nitrogen contained in raw water is finally oxidized to nitrate nitrogen via nitrite nitrogen by the action of nitrifying bacteria attached to Tohkemy’s original filler.
● By reducing ammonia nitrogen, which consumes a large amount of sodium hypochlorite, it is possible to suppress excessive injection of chemicals, and as a result, it is possible to suppress an increase in the concentration of chloric acid.
● Fillers and units can be combined according to the concentration of raw water ammonia, making it possible to handle high concentrations of ammonia.
|Installation space (L×W)||9.0×3.5m||10.0×4.0m||11.0×4.7m||5.5×14.5m||15.0×6.0m||16.0×6.2m|
|Air exposure tower||φ400mm||φ500mm||φ700mm||φ900mm||φ1000mm||φ1100mm|
|Air exposure tower treatment water tank||1m3||2m3||4m3||6m3||10m3||10m3|
|Ammonia removal tower||φ1000mm||φ1300mm||φ1900mm||φ2300mm||φ2600mm||φ2900mm|
|control panel||Outdoor self-supporting specification|
* Since the system configuration differs depending on the water quality, it is an option except for the basic system.
1-12-11 Tagawakita, Yodogawa-ku,Osaka
Overseas Business Department